The Owners of this mid-century Tucson bungalow home gave us a call after noticing symptoms of a foundation problem.
The Homeowners wanted to have the issue addressed and resolved to maintain the value of the home. There was also a concern about the cracking and popping noises the house was making.
An initial, Level A Foundation Inspection concluded a Level B, or forensic foundation inspection was needed.
Exterior Inspection: The exterior of the location was visually inspected. Items such as foundation cracks, exterior wall cracks, improper grading, type of structure, poor drainage, gutters or no gutters, bowed retaining walls, large trees close to the foundation and any type of obstructions that may or may not influence the repair process were noted and recorded.
Interior Inspection: The interior of the location was visually inspected. Items such as floor cracks, wall cracks, ceiling cracks, sloping floors, uneven counter tops, doors and windows that are out of alignment, cracked window glass and bowed walls were noted and recorded.
Manometer Survey: The manometer survey, also known as a floor survey, is a measurement of the differences of interior floor elevations. The flatness of the interior floor was measured using a highly accurate survey device known as a Manometer. The entire interior floor area was surveyed, and the elevations were recorded. These data points were then entered into a computer program that provides a topographical map showing the high and low elevation contours of the floor surface. This topographical map shows where the foundation is no longer level and shows where support and stabilization is needed. The floor survey also demonstrates whether any floor slab heave or settlement exists.
After examining the home and performing the manometer survey, Arizona Foundation Solutions believes the home could be experiencing foundation settlement at the southwestern portion of the main home as shown by the damage (aka Signs of Stress) and lower readings on the Topographical 2D Map. The drop off in floor elevations on the topographical map is consistent with a foundation settlement pattern. Foundation settlement can be caused by one or any combination of many factors, including: sub-grade saturation of moisture due to poor drainage, years of storm runoff, plumbing leaks, improper compaction, the lack of a proper foundation system, and/or (in most cases) natural earth movement.
AZFS also believes the home could be experiencing minor foundation settlement at the western and southeastern portions of the main home, and the western and southern portions of the addition as shown by the minor damage (Signs of Stress) and lower readings on the Manometer Data Points.
A minor heave pattern is observed in the eastern portion of the main home as indicated by the higher elevation readings on the Topographical 3D Map. This phenomenon usually occurs in areas where structures are built on expansive clays. Moisture from one or any combination of the following: storm runoff, poor drainage around the foundation, plumbing leaks and/or underground moisture sources will allow the moisture/vapor to accumulate underneath the foundation. The moisture then interacts with the clayey soils, causing them to swell. The clay soils take the path of least resistance and expand upwards and lift the foundation.
There are cracks in the patio slabs. When the slab cracks all the way through, the separate sections can move independently of one another.
Arizona Foundation Solutions believes that the proper way to permanently stop the perimeter foundation settlement is to underpin the areas that are experiencing movement. Underpinning is the process of installing deep foundation elements called piles. Piles are engineered foundation supports that are driven down past the unstable soils and are then locked up into load bearing strata, which can support the loads that are transferred to them. Once the piles have been installed, they can be used to lift the perimeter foundation up to it’s Highest Practical Maximum. The piles should be spaced approximately five to six feet on center and should start and stop near the hinge points of movement (exact spacing to be determined after load bearing calculations). In this case, the piles would be located at the southwestern portion of the main home. The slab can then be treated by injecting a lightweight expansive polyurethane to fill existing voids and lift the floor slab. This is done by drilling small 3/8” holes in the slab after which polyurethane grout is injected directly under the slab to raise it up to it’s Highest Practical Maximum. Using the expansive materials will help prevent additional slab settlement by compacting the upper layer of soil as it expands.
A protection plan has been designed to stop the western and southeastern portions of the main home, and the western and southern portions of the addition from any possible future settlement and further damages. AZFS can permanently stabilize this area at the Homeowner’s discretion.
AZFS does not suggest a heave repair plan at this time as there is no significant damage to correspond with the high elevation readings. The home should be monitored and should damage arise in the future, AZFS should be contacted to perform a comparative manometer survey at a discounted price.
Composite interlocking can be performed to tie the broken pieces of the concrete together. The existing cracks will be cleaned, and non-parallel lines will be cut across the existing cracks. Next carbon fiber laminate stitches will be inserted into the non-parallel cuts and then the gaps will be filled with a two part poly. Finally, the crack should be ground smooth to minimize the differential. If done properly, this will allow the slab to function as one unit. If this is instead expansion joint separation, the joint should be cleaned, routed, and re-caulked with an expansive joint filler. A determination as to which repair is needed will be made on site once the crack is exposed.
Since storm runoff is responsible for the majority of the moisture that pools next to the foundation, gutters need to be installed to prevent the storm runoff from increasing the amount of foundation movement. A proper gutter system should be installed to discharge the storm runoff a minimum of 10 feet, preferably 20 feet away from the foundation. We do not recommend installing gutters that discharge next to the foundation as this will only increase the probability of a foundation problem.
It is also beneficial to manage the moisture around your home using conventional means as outlined below:
Hire a reputable plumbing leak detector and repair service to check both pressure and sewer lines, this is usually done for less than $500. If repairs are needed, they are usually not expensive.
Make sure the grading of the terrain is sloped downwards at 5% slope from the home at all areas of the perimeter.
Stop irrigating plants that are near the foundation and make sure there is nothing trapping the moisture from flowing away from the home.
When permanently stabilizing, lifting and/or mitigating a foundation movement problem, AZFS recommends waiting AT LEAST 6 months before investing in cosmetic repairs.
Safety or Structural Concerns: None
Engineer: Néstor J. Brea